The interconnecting strips enable more MCB´s, switches and protective switches to be interconnected between each other. With the interconnection of our current protective switches BONEGA®EV6P with the MCB´s BONEGA® PEP or BONEGA®EV6J, you can assemble an associated electrical device which is always cheaper than the compact devices with the same function. We supply the copper 1, 2, 3, 4pole interconnecting “reed” strips with insulation, and the 1pole and 3pole forked types.
The insulation is made of ABS see Comparison of ABS, the selfextinguishing ABS VO and PVC (in )
The strips are supplied either with the crosssections of 16 mm^{2} or 10 mm^{2}, always with insulating material made of selfextinguishing ABSVO. The copper contacts (reeds) are located closed at the strip edges. See our offer of MCB´s accessories.
The singlepole MCB´s can be interconnected also in the socalled “German” way, i.e. with a special strip without any insulation. When accepting this method, it is necessary to break off both barriers against the interphase shortcircuit (see protection against an interphase shortcircuit).
Technical Data 

Number of poles:  1,2,3,4 
Supplied length:  1 m 
Load current:  80 A 
Material of the strip:  Copper (ECU  F25) 
Material of insulation:  Selfextinguishing ABS  VO (PC/ABS Biend UL 94  VO) 
Compliance with the standards:  DIN EN 60 4391: 1994 a VDE 0660, part 500 
Shortcircuit resistance:  25 kA 
Strip crosssection:  16 mm^{2} 
Dimensions of a reed:  4 x 12 mm 
Insulation resistance:  36kV/ mm 
Mechanical resistance of the insulation pursuant to the standard : 
IEC 68 2 
Rated voltage:  415 V 
Operative voltage:  max. 500 V 
Max. load:  4 kV 
Parameters of the interconnecting strip ampere load 

1 phase /two interconnected strips  2,3 and 4 phase / two interconnected strips  
Interconnecting strip’s crosssection in mm2 
10  12  16  20  25  36  10  16  25  36  
Power supply from the strip’s edge, max. current Is = A 
63/ 126 
65/ 130 
80/ 160 
90/ 180 
100/ 200 
130/ 260 
63/ 126 
80/ 160 
100/ 200 
130/ 260 

Power supply in the middle of the strip Max. current Is = A 

100/ 200 
110/ 220 
130/ 260 
150/ 300 
180/ 360 
220/ 440 
100/ 200 
130/ 260 
180/ 360 
220/ 440 

Singlepole copper interconnecting strip with contacts at the strip’s edge
There are 57 contacts on the length of 1 m. 


Twopole copper interconnecting strip with contacts at the strip’s edge
There are 56 contacts on the length of 1 m. 


3pole copper interconnecting strip with contacts at the strip’s edge
There are 54 contacts on the length of 1 m. 


4pole copper interconnecting strip with contacts at the strip’s edge
There are 56 contacts on the length of 1 m. 

Plastic strip terminal head for 2 and 3 pole stripsCode of Order: 08  1011


Singlepole copper interconnecting strip with contacts at the strip’s edge
There are 55 contacts on the length of 1 m. 


3pole copper interconnecting strip with contacts at the strip’s edge
There are 54 contacts on the length of 1 m. 



Plastic strip terminal head for 3 pole stripsCode of Order: 08  0011

Export Manager: Michal Hudeček, tel: +420 605 518 724, michal.hudecek@bonega.cz
Sales Department:  Mrs Libuše Možnarová, fax +420 518 335 216, email : libuse.moznarova@bonega.cz, 696 66 Sudoměřice nad Moravou 302

Products  About us  Customer support  Become our partner  Certificates & declarations  Contacts  Site map 
, Potoční 302, 696 66 Sudoměřice nad Moravou, Czech Republic, michal.hudecek@bonega.cz, tel. +420 605 518 724 